contact usContact Us
Changzhou Chaokang Machinery Co., Ltd. Contact: Ge Lei Phone: 18068771880
Factory Address: Anjia Industrial Park, Chunjiang Town, Xinbei District, Changzhou Office Address: Room 1513, Building 4, Tianyu Plaza, Xuejia Town, Xinbei District, Changzhou, Jiangsu
The emergence of the PP waste gas tower has brought great benefits to the enterprise. The waste gas is blown in from the bottom of the tower, and comes out from the top. The inside is filled with spray water. The spray water is sprayed from above. Absorb, and then remove the ingredients absorbed in the water. However, pay attention to the following points when using the exhaust gas purification tower:
1. The PP exhaust tower should be installed on the concrete foundation more than 100mm above the ground, and the pump and fan should be used as another concrete foundation as required.
2. Pay attention to maintenance when transporting the device, and do not damage the body and components.
3. When the pp purification tower leaves the factory, the company will deliver it in sections according to the specific situation, and the company will send personnel to the on-site device for debugging.
4. For exhaust gas purification tower installations and operations outdoors, pay attention to freezing prevention in the bottom pool in winter.
5. The tank at the bottom of the device has a liquid level symbol. Before use, be sure to inject the absorption liquid according to the liquid symbols. Pay attention to replenishing the absorbent during use.
6. When the PP exhaust tower is in operation, the circulating water pump should be turned on for 2-3 minutes, and then the blower should be started. When stopping, the blower should be stopped for 1-2 minutes before stopping the circulating water pump.
7. The acidic depth of the liquid in the pool at the bottom of the tower and the degree of gas purification at the exhaust port should be regularly checked according to the operating situation, when it exceeds the standard. The absorbent in the bottom tank should be replaced.
8. The exhaust gas purification tower should be overhauled once a year and a half to two years, check the plugging conditions of the disc-shaped spray pipes and fillers, and clean them.
The above is the introduction of Changzhou Chaokang Machinery Co., Ltd. We look forward to cooperating with you.
You might also be interested in